The amount of time that it will take for water landing on the roof area to enter the system. The inflows from the area will then be evenly spread over this time when the area is analysed.
This amount of time can be calculated with the Time Of Concentration Calculator.
The analysis is the same as the Time Area Diagram method with the time area diagram being built with an even spread of the area over the time of concentration.
Eg. Time of Concentration = 3 mins, Area = 0.75ha
If the timestep is 1 minute, A1 = 0.25, A2 = 0.25, A3 = 0.25.
The rainfall profile and the time area diagram are combined with the volumetric runoff coefficient in the following way:
Q_{1} = (I_{1} x A_{1}) x 2.78 x C_{v}
Q_{2} = (I_{1} x A_{2} + I_{2} x A_{1}) x 2.78 x Cv
Q_{3} = (I_{1} x A_{3} + I_{2} x A_{2} + I3 x A_{1}) x 2.78 x Cv
And so on…
Section Pages |
Workflow - What's next...?
Inflows connect to either Junctions or Stormwater controls via Inlets. Specify an Outlet on these objects then choose to connect to another Junction or Stormwater Control.